User Configurable from 0 to 32 Seconds (via Digital Communication).
Operating Temperature - Display
-20° to 80° C (-4° to 176° F)
-40° to 85° C (-40° to 185° F); without damage
-40° to 100° C (-40° to 212° F)
mV (-10-100 mV) TC (NBS: E, J, K ,N): ±0.03% of the input mV or 0.01 mV whichever is greater -10° C variation
mV (-6-22 mV), TC (NBS: B, R, S, T): ±0.03% of the input mV or 0.002 mV whichever is greater -10° C variation
Ohms: 0 to 400 Ohms, RTD (IEC: Pt100): ±0.03% of the input resistance or 0.04 Ohms, whichever is greater
-40° to 85° C (-40° to 185° F)
0 to 100% Relative Humidity
±0.02% of span
Span and Zero Adjustments
Non-interactive, via local Adjustment and Digital Communication.
±0.1% of Reading or +0.1° C (0.18° F), whichever is greater, for 1-year for thermocouples.
±0.1% of Reading or +0.1° C (0.18° F), whichever is greater, for 2 -years for RTDs
Electromagnetic Interference Effect
Approved according to IEC61326-1:2006, IEC61326-2-3:2006, IEC61000-6-4:2006, IEC61000-6-2:2005
Available sensor connection types below, 3-wire is standard.
Power Supply Effect
±0.005% of Calibrated Span Per Volt
HART: 12-45 Vdc.
HART: 2-wire, 4-20 mA according to NAMUR NE43 specification, with super-imposed Digital Communication.
2-wire 4-20 mA
Available display types below, no display is standard.
4-1/2-Digit Numerical and 5-Character Alphanumerical LCD Indicator
HART: In case of sensor or circuit failure, the self diagnostics drives the output to 3.6 to 21.0 mA, according to the user's choice & NAMUR NE43 specification.
HART: By Digital Communication using the Configuration software CONF401, DDCON100, or HPC301 and HPC401. It can also be configured using DD and FDT/DTM tools, and can be partially configured through local Adjustment, since the transmitter is supplied with display.
Control Functions Characteristics
HART: PID Control, Alarm and Set Point Ramp Generator
Available mounting types below, no mounting is standard.
316 Stainless Steel Bracket and Accessories
Can be attached directly to the sensor. With an optional bracket can be installed on a 2" pipe or Fixed on a wall or panel.